However, strand control is recommended when installing multiple panels.
Steel ventilation plates with a free cross section of 51% have to be installed.
Yes, as long as it is a common raised-floor grid of 600 x 600 mm
he HydroLogic Panel weighs 35 kg, the HydroLogic V 70 kg.
-450 mm for the HydroLogic panel
-600 mm for the HydroLogic V
A simple control for up to 4 different temperature ranges. For a higher quantity a PLC control is used.
Depending on your wishes, either the setpoint temperature in the cold aisle or the setpoint temperature in the warm aisle is controllable.
Will the panels be placed in the cold or hot aisle?
The fan is designed to suck the warm air into the raised floor. This happens regardless of whether it is installed in the cold aisle or the warm aisle.
The air cycle is comparable to a climate chamber only without the long way to the end of the hall.
Yes, it is the most efficient cooling method for air-cooled servers.
Since the heat exchanger is placed in close proximity to the heat generator, time-consuming air transport is eliminated.
The device is maintenance-free
In the V-Variation a DX is available.
With the HydroLogic V it is possible to drain the condensate.
The HydroLogic Panel has no condensate management. Here, the temperature of the cooling water remains above the dew point, whereby no condensate management is necessary.
With a Mollier H-X diagram.
Yes, the system is compatible with all common variations.